الحمد لله والصلاة والسلام على رسول الله وعلى آله وصحبه أجمعين EQUIPMENT DETAILS Water Booster pump SCHEDULE OF PLANNED PREVENTIVE MAINTENANCE Work Plan EQUIPMENT DETAILS Water Booster pump صيانة دورية جداول جاهزة نظام مضخة زيادة ضغط الماء Capacity Qty: Lot Make & Model Location Smoke Fan Water Booster pump Task Description W / Weekly M / Monthly Q / Quarterly SA/ Semi/Annually A/ Annually SST / Seasonal Start/Up SSH / Season Shut Down 2W M 3M 6M A Notes Item Description Qty Notes Critical Tasks Operate manually all pumps Examine water and air pressure gauge Check all valves for free travel Test audible alarm Check glands for leaks if necessary tighten Inspect unit for unusual noise and/or vibration, ensure that it is in good working order. Provide lubrication, if necessary. If unit is not running or an identified problem requires the unit to be serviced, perform ALL Non- Critical Tasks listed below. Flush and clean strainers. Check operation of gauges and record pressures and temperatures. Inspect seals and packing, tighten or replace as necessary. Lubricate impeller shaft bearings. Inspect motor and pump alignment. Other recommended tasks Inspect mounting bolts and vibration isolators of the pump under load conditions. Start and stop pump, noting any vibration and overall performance. Inspect drive shaft coupling. Operate manually all pumps Check all valves for free travel Examine water and air pressure gauge Test audible alarm Check glands for leaks if necessary tighten Clean all strainers Examine pipe work & connection for leak Lubricate all bearings Blowout all dust from control panel, pump and motor Check alignment ( coupling ) Check all operating control if necessary adjust Check for necessary paint Notes Use additional sheets if required PPM routines based on Complete Running hour where recommended by the Manufacturer http://www.sitei.net/up/do.php?id=57 في أمان الله !